RIBXGTA | Enclosed Split-Core AC Sensor, .75-150Amp, adjustable, terminals | Functional Devices
Details for RIBXGTA
Enclosed Split-Core AC Sensor, .75-150Amp, adjustable, terminals
The SCAL unit begins the 30 second self-calibration process the first time current is applied in the operating range. The threshold is then set. Subsequent calibrations may be performed by moving SW1 to the position opposite of its current position with or without current applied (hands can be safely away from live voltage). Once current begins flowing, or if it already is, the calibration process will begin. At the end of the 30 seconds, amperage will be read and set as the threshold. SW2 in the ON position provides a 15% (+/-3%) differential. In the OFF position, it provides a 25% (+/-3%) differential. SW2 can be selected at anytime and does not affect the threshold setting. Current in-range closes the sensor contact. Current above or below range opens the sensor contact.
|Current Core||Split Core|
|Current Switch Type||Solid State|