140221 | Premier Series 2-Zone Control Panel 2H/1C | Braeburn
Details for 140221
Premier Series 2-Zone Control Panel 2H/1C
Braeburn Zone Control Panels Featuring a compact 8”W x 6”H housing and a large 3 sq. in. backlit display for set-up, checkout and operation.
Quick and Easy Installation Push-in terminal blocks lock in wires without a screwdriver. LED’s indicate equipment and zone calls while the display keeps you up to date with panel operation. Plus, wire guides and a small footprint allow for a quick and professional installation
Product Features and Benefits
- Controls up to 2 heating and 1 cooling stage
- Compatible with electric, gas, oil and heat pump equipment–including dual fuel
- Can be used with virtually all low-voltage thermostats and dampers from other manufacturers
- Large 3 sq. in. display shows system status
- Dual fuel operation with Braeburn outdoor sensor
- LED’s show all calls at a glance
- Push-in terminals for easy wiring– no screwdriver needed
- Flexible staging controlled by panel or thermostat
- Push button set-up without dip switches
The fully automatic zone panel shall be Braeburn model number 140221, 8.0”W x 6”H x 2.1”D, powered from 24 Volts AC. In the event of a power failure, the unit shall retain all configuration settings. The zone panel shall be compatible with low voltage mechanical or electronic thermostats and be capable of controlling up to two stages of heating and one stage of cooling. Wiring blocks with terminals R, Y, W1/E/AUX, W2/O/B, G, and L shall be included for two thermostats and a selectable emergency heat position. Equipment terminals Rh, Rc, Y, W1/E/AUX, W2/O/B, G, L and C shall be present along with two sets of damper terminals PO, C, and PC. Configuration options shall be available for System Type-1st Stage/2nd Stage Fan Control for Heating, Reversing Valve, Auxiliary Stage Heat Compressor Lock, Set EM heat Zones, Compressor Balance Point, Auxiliary Balance Point, Fan Purge Time, Thermostat Type, Equipment Staging Criteria, Staging Lock, Thermostat Able to Activate EM Heat, Zone Priority, Short Cycle Protection, Temperature Scale, Opposite Mode Call Timer, Address Clear. LED’s (Light Emitting Diodes) shall be present to monitor Panel Power (1), Panel Processor (1), Emergency heat (1), HVAC equipment terminals (7), two inputs for two thermostats (12), and outputs for two dampers (2). Provisions shall be available to display and adjust high and low temperature cut out and short cycle protection override. The panel shall have an operating temperature of -22 to 167°F (-30 to 75° C), and a storage temperature of -40 to 167°F (-40 to 75° C) with an operating humidity range of 5 to 95% RH non-condensing.